If the power is off,
|Continuity guarantee |
Plug & Play.
|Rapid status |
|COMPACT AND MODULAR||MULTI-FUNCTION SYSTEM||LOCKING AND SAFETY|
|It is installed as any other RCCB. No additional connections between the motor and switch are needed.|| |
Mechanism on the front panel used to switch the RCCB ON/OFF, reset the resetting counter and lock the unit.
|Locking system that sets operation to the automatic or manual mode. Sealable.|
Keeps the installations
|Second homes, refrigerators, alarms, garage doors, etc.|| |
Air conditioning, refrigerating chambers, lighting, UPS, etc.
|Control of production processes, etc.|
Incredibly easy to install
Complies with all requirements for household and similar automatic resetting devices described in the EN 50557 Standard..
Disconnect the main switch of the installation (IGA). ¡Important! Do not tamper with the voltage circuits.
Next, remove the protection cover from the electric panel.
Disconnect the RCCB to be replaced from the terminal.
Replace it with the new REC3 self-resetting switch.
Connect the input and output terminals of the switch. It is now installed!
Finally, connect the IGA.
Press the TEST key to check the correct operation of the REC3 before putting the protection cover back on.
Put the protection cover back on the electric panel to complete the installation. As easy as it looks.