The CVM-E3-MINI-WiEth power analyzer lets you gather information on the energy consumption and electrical parameters of your installation quickly and easily. It has Ethernet and Wi-Fi communications that provide real-time information to the Energy Management System (EMS), without having to install wiring for communications.
Its Bluetooth connectivity can be used to set up communications parameters (Ethernet or Wi-Fi) through the free MyConfig app on your mobile or tablet, without having to physically access the device.
Connect the analyzer to your Wi-Fi network and start registering all your consumptions and electrical parameters from your installation. Check the Wi-Fi coverage and assigned IP address directly from its display.
Connect the analyzer to your Wi-Fi network and start registering all your consumptions and electrical parameters from your installation. Quickly check the device IP and MAC address by its display any time.
Use Bluetooth connectivity to program Ethernet or Wi-Fi communications without the need for a computer.
With the free MyConfig app, you can set up the communications on your power analyzer quickly and easily.
The CVM-E3-MINI-WiEth Power Analyzer lets you know the consumption of active, reactive inductive, reactive capacitive and apparent energy as well as record and display the cost of energy, CO2 emissions and operating hours for preventive maintenance. The device has measurement in 4 quadrants so it also accumulates these same variables in energy generation.
Install it in panels to verify the quality of consumption of your installation, since in addition to electrical variables such as voltage, current, power and power factor (monitors more than 250 variables) you can also check the distortion caused by the harmonics present in your installation both at a total level through the THD% and checking each harmonic individually up to 31º in voltage and current.
The flexibility of the CVM-E3-MINI-WiEth analyzer allows you to set up your communications quickly, safely and easily. You can do this in the following ways:
Solve any error in the programming or physical wiring of the analyzer through the PowerStudio software. Saves on indirect costs in commissioning and configuration.
The voltage wiring must correspond to the current wiring of the same phase. If this does not happen, it means that the installation has been performed incorrectly. This will cause values such as power, cos phi, PF or energies to be incorrect.
The installation of the current transformers must be correct, following the flow direction of the load. If a transformer is installed reversed, the current will be displayed as generated current instead of consumed or vice versa, having an error in the total energy register.